LANTNAVFACENGCOM A&E GUIDE
See Table T-2 for guidelines in using the building design energy target.
Justification/rationale is required should the annual energy consumption estimate
exceed the design energy budget target.
ENERGY CONSERVATION SUBMITTAL REQUIREMENTS
(See Flow Diagram, Section 4.6.4)
A. 15% Submittal. Forms S-1 and E-1.
B. 35% Submittal. Energy Analysis and Life Cycle Cost Analysis (Form
C. 100% submittal. Form MS-1.
HEATING PLANTS AND HEATING PLANT ADDITIONS
A. Before stating the type of fuel to be used and an economic comparison of
the selected fuel with other available fuels, contact the LANTNAVFACENGCOM
Mechanical Engineering Branch for the latest criteria for fuel selection.
Describe new boilers including size, pressure and type.
C. Describe any new auxiliaries to be added and what source of power will
be used for their operation.
D. Describe the fuel storage and conveying system to be installed.
E. Describe the safety and combustion control systems utilized and how they
REFRIGERATION (COLD STORAGE)
A. Identify areas to be refrigerated, indicating their usage and temperatures
to be maintained.
Describe type of refrigeration equipment and systems.
FUEL DISTRIBUTION AND STORAGE
(1) Describe type, location of take off from supply, and available pressure.
(2) Identify type and materials for pipe and valves.