LANTNAVFACENGCOM A&E GUIDE
Shop drawings for the systems, equipment, and materials listed in Section 8
shall ALWAYS be designated for Contracting Officer approval. The specific systems,
equipment, and materials must be listed in the technical sections of the specifications.
The standard 16 Division Construction Specifications Institute format shall be
used on all projects. On small projects or projects of a special nature using only a few
divisions, the listing of non-applicable divisions may be omitted.
Control Diagrams - Provide a written sequence of operation for each
mechanical and electrical control system stating explicitly how systems are to function.
Give all pertinent data regarding safety, alarms, indicators, and control parameters.
The sequence of operations may be shown on the control diagrams in lieu of in the
C. FINAL SUBMITTAL. Following the review of the prefinal submittal,
comments and corrections to be included in the final submittal will be furnished to the
A&E by LANTNAVFACENGCOM. The final submittal to LANTNAVFACENGCOM
shall consist of one complete specification manuscript on bond paper, single spaced,
and typed on one side only, and two bound photographic copies. Do not bind the
bond manuscript but do bind the conies. In addition, provide one copy of project
submittal register and test requirements report and provide floppy disks containing the
SPECSINTACT version of the entire specification sections, as well as submittals
processing, reference processing, and related operations.
PROTECT SUBMITTAL REGISTER:
Provide the submittal register, which is a list of all submittals required for
the project, using the SPECSINTACT system.
TEST REQUIREMENTS REPORT:
Provide the test requirements report, which is a list of all testing required
for the project, using the SPECSINTACT system.
In order to ensure an award being made within available funds, additive bid
items will be established by the A&E in conjunction with the PM and the station;
however, additive bid items are not required whenever the project cost estimate is
clearly within the funds available.