horns or audio-visual
Evacuation signals shall be resonating
shall be located as
devices with no less than 90 db at 10 feet and
so fire alarm is audible
shown on the drawings. Horns shall be located
of a building.
over all background noise throughout all areas
1. All Wiring shall be in accordance with the National Electrical
Code and National Fire Protection Association Standards Nos. 71, 72A,
72B, 72C, and 72D, latest editions.
TESTING, GUARANTEE AND SERVICE:
1. A representative of the manufacturer shall supervise the final
testing of the system. Final testing shall be witnessed by the
PACNAVFACENGCOM Fire Protection Engineer who will recommend the system
for acceptance or nonacceptance to the Contracting Officer. On
completion of the acceptance tests, instructions shall be given in the
operation and testing of the system.
2. The fire alarm system shall be free from defects in workmanship
and materials, under normal use and service, for a period of one year
from the date of acceptance. Any equipment proved to be defective la
workmanship or material shall be repaired, replaced, or adjusted free