Batteries shall not be in the same room as the UPS modules.
The UPS module shall not be located in the mechanical room.
g) Provide the correct number of power conductors as indicated on the
h) Proper the proper number of shielded control conductors indicated on
the installation drawings.
i) Provide battery conductors/jumpers sized as indicated on the
j) Indicate on the floor plans and one line diagram the maintenance
k) The room containing the UPS module shall be ventilated and not air
One ventilation motor shall be placed over the UPS module.
m) Provide separate buses for the UPS input and by-pass supplies as
indicated in MIL-HDBK-1004/1.
Provide grounding detail for UPS/Generator/Main Service.
The battery room is not to be considered a hazardous area.
p) Provide a detailed breakdown in the specifications of the
contractors responsibilities and requirements for UPS installation and start-
q) Install an even number of positive and negative conductors in each
RGS conduit battery circuit to avoid excess battery voltage dip when battery
assumes load. Single polarity runs shall be in PVC.
r) Emerson UPS must always have a neutral conductor run with the by-
s) The remote monitor has a circuit length limit of 500 feet from the
a) Hookstick operated equipment: The A/E shall check if ACTIVITY
personnel are available/trained to operate.
Design Submission Requirements
(NOTE: SEE THE CHAPTERS TITLED "PREPARATION OF DRAWINGS", PREPARATION OF
SPECIFICATIONS" AND "PREPARATION OF DESIGN ANALYSIS" FOR GENERAL CONTENT
REQUIREMENTS REGARDING PREPARATION OF THE DOCUMENTS LISTED BELOW)
Submit the following:
a) Basis of Design: A discussion in report form of how the A/E's
concept satisfies the user requirements, meets criteria and is cost effective.
Include the following: