Is building considered windowless?
HDBK-1008A, Paras 18.104.22.168
If so, are sprinklers provided?
Is roof covering or deck assembly allowed?
HDBK-1008A, Sec. 2.8
Are smoke and heat vents needed?
HDBK-1008A, Para. 2.11.3
Is access provided for firefighting within
HDBK-1008A, Sec. 2.10
Is access provided for fire vehicles around
(See local fire Dept.
Is interior finish material in compliance
HDBK-1008A, Sec. 2.6
(walls, ceilings)? Is restriction against
plastics complied with?
Is floor carpet properly specified?
HDBK-1008A, Sec. 22.214.171.124
Is insulation properly specified?
HDBK-1008A, Sec. 2.7
Does insulation in concealed spaces of sprink-
NFPA 13, Para.126.96.36.199
lered building have a flame spread of 25 or less
and a smoke developed rating of 50 or less?
BUILDING SEPARATION/EXPOSURE PROTECTION
For the building in question and adjacent
UBC, Secs. 505 and 506,
building(s) is the combined floor area
in excess of that allowed?
If the answer above is yes, buildings must be
HDBK-1008A, Sec. 2.3
separated by distance. If the buildings
cannot be separated by distance, fire
resistive walls must be provided on
13 of 22