Roof framing plan
Floor framing plan
Foundation layout plan
d. Design notes (live load, wind, seismic, etc., and materials design
220.127.116.11 Explosives Safety:
Identify threat and give distance or negative
a. Location description, size and capacities of all mechanical
b. Large scale plan and sections of equipment rooms showing layout of
equipment, ductwork, piping and adequate space around equipment for
a. Layouts of air conditioning or ventilation ductwork and piping
systems. Ductwork shall be shown double line. Provide flows (CFM & GPM)
at each outlet.
Plumbing fixtures and isometric or riser diagrams.
System and control diagrams for mechanical systems.
Routing and capacities of distribution systems.
Energy analysis and studies.
Basis design and design analysis.
Economic analysis and life cycle cost studies.
Label drawings FPM-1, etc.
b. Sprinkler system drawings shall be performance oriented drawings,
i.e., specific pipe runs, head locations, hanger details, etc., are not to
be shown. Show underground pipe connection to street mains; sprinkler
riser location and minimum size; a riser detail; and legend notes
indicating hydraulic design point(s) along with available water supply
c. Fire pump drawings will show equipment layout; pipe layout and
minimum pipe sizes; pumps; drivers; control panels; water flow meter size