50% completion. Interior demolition should
be shown on separate plan.
Transformation to Secondary Service:
b.Site Plan: This plan should be developed to
1) Primary and secondary voltage rating.
2) Describe the transformer or unit
approximately 50% completion. Information
on existing conditions should be complete and
3) Describe the proposed primary and
c. Lighting Plan(s): These plans should
4) Describe the proposed primary and
show a building's full floor plan (first, second,
etc.) with the layout and type of fixtures to be
secondary protection devices.
used and the design footcandle levels for all
c. Describe the Electrical Systems
types of lighting systems.
including the following:
d.Power Plan(s): These plans should show a
1) Lighting systems
2) Power systems
building's full floor plan (first, second, etc.)
3) Emergency lighting
4) Emergency power
5) Grounding system or systems
transformers and any other major equipment
6) Telephone system
throughout the inside and outside of the
7) Other systems such as television,
building or project.
paging, call, etc.
e. Single Line Diagram: This drawing
8) Physical and electronic security features
should be developed to approximately 50%
such as IDS, lighting access control,
completion showing all panels, switchboards,
motor control centers, transformers and other
d.A statement describing proposed
major electrical loads such as M.G. sets, A/C
pertinent standards of design, such as
voltage regulation, lighting intensities, and type
f. Additional Plans/Risers (Show Location
of lighting fixtures.
2.2 35% DESIGN SUBMITTAL: The
35% Design Submission shall include the
3) Others as required
35% Design Data:
a. Preliminary Drawings.
b. Design Data (Basis of Design, Design
184.108.40.206 35% Electrical Basis of Design:
Calculations and Economic Analysis, if
See paragraph 220.127.116.11 for requirements.
18.104.22.168 35% Design Calculations: Refer to
SODIV-TG-1004 for required calculations.
a. Existing Site and Demolition Plan: This
plan should be developed to approximately
ELECTRICAL SUBMITTAL REQUIREMENTS