Custom Search




MILHDBK419A
The step voltage near the lofoot by linch (3.05 m x 2.54 cm) rod in 1000 ohmcm soil is about 68 percent of
the voltage between the rod and a point approaching an infinite distance away. Step voltage near a ground rod
will be between 80 percent of the rod potential (for very short rods) and 50 percent (for very long rods).
The step voltage on the surface of the earth near an isolated lofoot by linch (3.05 m x 2.54 cm) ground rod
= 1000 ohmcm) carrying a lightning current of 20,000 amps could be fatal since the step voltage would be
(261)
which is 41 times higher than the safe step voltage derived above.
The resistance of the 10foot by 1inch (3.05 m x 2.54 cm) rod in 1000 ohmcm soil is
(262)
Higher values of earth resistivity would cause the step voltage near the rod to be even higher than the
calculated 41,400 volts. For a three second duration shock condition, the requirement that the step voltage not
exceed 100 volts means that the single 10foot by 1inch (3.05 m x 2.54 cm) rod would produce an unsafe Step
voltage with a fault current greater than about 50 amperes, even in low resistivity (1000 ohmcm) soil.
251


Integrated Publishing, Inc.
6230 Stone Rd, Unit Q
Port Richey, FL 34668
Phone For Parts Inquiries: (727) 4930744 Google + 