PART V - SIGNAL REFERENCE SUBSYSTEM GROUNDING
Visually inspect the signal reference subsystem for compromises
in violation of the recommendations of Section 1.5.
Inspect connections to equipment signal ground terminals
(see Section 188.8.131.52.2) and equipotential plane for looseness
and corrosion. Apply corrective measures.
Check to see if any new equipments have been added or relocated
since the last inspection. If so, check interconnecting cables
for conformance with the requirements of Section 1.5.
Insure that labels and protective covers are in place and free
of serious damage.
Inspect equipment grounding cables (see Section 1.5) for correct
sizes, physical damage, and properly bonded end connections.
Record all deficiencies below:
Corrective Action Taken
Ground System Point-to-Point Resistance (See Section 184.108.40.206.5 for selection of measurement locations):
Attach Results of Ground System Noise Survey. Carefully compare results with those obtained during
previous inspection to detect noticeable and significant changes in voltage and current levels.