Are all hand rails, ladders, stairways, antenna pedestals, and other objects
subject to human contact grounded?
Are power lines at the point of entry to the facility protected with approved
Are overall cable shields grounded at each end?
Do any bonds show any signs of corrosion?
Are all bolted or threaded fastener bonds adequately torqued?
MIL-STD-188-124A, 18.104.22.168 and 22.214.171.124; Table 1-23
Do any bonds have high resistance across the bond?
Are C-clamps or spring clamps used for bonding?
Are bonded areas visually clean?
Is each subassembly and chassis adequately bonded to the rack, frame, or
Are cable connectors adequately mounted?
Are shields of coaxial cable adequately fastened?
Are shield pigtails less than 2.5 cm (1 inch) long?