If this is not possible, or the RF noise in a particular area is too high, use shielded
cable. Ground the shield to the control cabinet only!
See below for information on sensor wiring connections.
Never mix 3K and 10K controls and sensors. System operation and
performance will be seriously affected. See Sections 4.3.1 and 4.3.2
for more information.
Before replacing an apparently defective sensor, try to determine why it failed. For
example, if the sensor location is wet, the new sensor will also fail rapidly.
5.2 REPAIR PROCEDURES