TM 5-683/NAVFAC MO-116/AFJMAN 32-1083/
Table 15-3. Interior wiring and lighting system.
Unauthorized or nonstandard attachments
Defective convenience outlets and switches.
Proper fuse sizes in panels.
Overheating of panels.
Any condition likely to cause fire. Check battery-
type emergency lights and replacement lamps.
Check for Iamps larger than standard prescribed
Replace burnt out lamps in hard-to-reach places.
(To be accomplished by electrical shop if special
equipment such as ladder trucks are needed).
Panels for circuit idenificaton and accessibility.
Replace blown fuses.
Replace burnt out or defective incandescent lamps.
Replace burnt out fluorescent lamps if personnel
have been instructed in this function and if assigned
to user. Promptly replace or report defective
lamps since a lamp approaching bum out flashes on
and off, causing overduty on auxiliary equipment.
Make repairs and adjustments to systems when
malfunctions are reported. Ensure that all work
complies with the NEC
Check ground resistance for special weapons
facilities at request of user.
Check for low voltages and/or low power factor.
Inspect station (substation switchgear or UPS) as
(1) Check electrolyte level and add distilled water if
(2) Check charging rate. Adjust charging rate as
necessary to maintain proper specific gravity.
(3) Test for proper operation under simulated
power interruption. Check maintenance free
batteries. Check voltage, check and clean