LANTNAVFACENGCOM A&E GUIDE
(3) For projects geographically located within the Continental United
States (CONUS) involving new water distribution systems, new wastewater pump
stations, or distribution systems, submit the following to the appropriate State
regulatory agency for review: Basis of Design (1 copy); plans (3 copies); and outline
specifications (3 copies). Each element shall be clearly marked "PRELIMINARY". The
PM will receive a copy of the transmittal letter forwarding each submittal.
A. PURPOSE: A technical review is required to ensure compliance with
Navy, DOD and Non-DOD requirements, constructability adequacy, and a functional
check. The A&E should submit plans and specifications in final form from his
viewpoint, thus preventing time-consuming reviews of incomplete plans and
EACH 35%, OR PREVIOUS, REVIEW COMMENT SENT TO THE A&E
SHALL BE RETURNED WITH EACH COMMENT ADDRESSED. IF THE COMMENT
WAS INCORPORATED INTO THE DESIGN, A RESPONSE SHALL SO INDICATE. IF
THE COMMENT WAS NOT INCORPORATED, AN EXPLANATION SHALL BE
PROVIDED FOR NOT DOING SO.
(1) Plans - coordinated, checked, and complete from the A&E viewpoint
(except for LANTNAVFACENGCOM and NAVFACENGCOM drawing numbers).
(2) Mechanical Drawings - Area for tube, coil, filter, etc., removal must be
shown dotted and labeled. Piping and equipment isometrics should be included for all
but the simplest systems. If space is limited, show dotted in major equipment from
other trades; air compressor, domestic hot water heater, electrical panels, etc. Consider
use of 3-D isometric layout for spaces that are crowded. Prior to final submittal an
overlay should be made of plumbing, mechanical, electrical and communication
equipment in the space to verify required clearances and access space. The sequence of
operation for the automatic temperature control system should be shown on the
(3) Color Design:
(a) Finish schedule with color code columns completed with the
appropriate color codes.